New Schneider Electric Research Details How Higher Chilled Water Temperatures Can Improve Data Centre Cooling and Energy Efficiency by 64%
The link to the original content can be found at the end of our message below.
In the past Forimmediaterelease circulated releases distributed through the Cision and PR Newswire system on a complimentary basis and as a service to our readers.
PR Newswire now claims copyright on press releases distributed through the Cision and PR Newswire system.
Their pitch: “Share your brand’s story around the world,” but that’s where it ends. When eTN, as a media outlet for travel and tourism news, tried to publish a release distributed to journalists by PR Newswire, they were told the release must be removed immediately. In addition, PR Newswire threatened eTurboNews with their legal counsel claiming copyright of releases from PR Newswire or Cision circulates on behalf of clients.
Here is the letter received by eTurboNews from a PR Newswire/Cision director:
“Subject: removal request
Please immediately remove the following posting from your site: [website name removed]
PR Newswire distributed this release on behalf of our client [client name removed]
[company name removed] is understandably upset that the release is posted on your site, tagged with Travel & Tourism Industry release: at the start of the text.
As you can see below in the release that we distributed that we did not include any coding or tagging on our end to indicate that the release is relevant to the Travel & Tourism industry: [website link removed]
Please completely remove the posting from your site as soon as possible, and confirm when complete.
Additionally, I am unable to find a licensing agreement between PR Newswire and eTN, or any other associated websites. If you do have a licensing agreement in which PR Newswire has licensed your sites to publish our content, please send a copy to me as soon as possible.
If you do not have a licensing agreement, we request that you remove all PR Newswire content from all of your sites. If I should have our Counsel send an official request, please let me know to whom it should be resent.
Director CISION PR Newswire”
It appears PR Newswire is not only charging a steep amount of money from companies wanting their releases circulated through their system to journalists but also is now trying to license this content as their copyrighted material. eTN receives more than 2,000 story ideas on a daily basis, we don’t rely on PR Newswire for content, and for sure we won’t pay them a licensing fee for a ‘privilege’ to publish such content.
We urge everyone using PR Newswire services to take a look at this article explaining their modus of operation and misleading reports: http://buzz.travel/prn/ .
PR Newswire is now directly competing with publications. This will result in a drastic drop in pick-ups. They are obviously upset with the attention we received for stoties and the visibility we were able to record way ahead of PR Newswire when it comes to our industry segment.
Journalists of any publication should be warned to consider taking content from PR Newswire or Cision.
Therefore, in the future, if you would like us to consider your press releases for publication, you will need to send it to us directly: For more information, visit: www.buzz.travel .
As a courtesy to our readers, you can find the original release content at:
LONDON, May 17, 2018 /PRNewswire/ —
- A study of two data centres found that utilising higher temperatures resulted in energy savings of between 41% and 64%, whilst driving significant improvements in PUE
- A small increase in capital expenditure for additional air cooling systems, redesigned cooling coils and additional adiabatic coolers is offset by reduced energy costs
- Payback in terms of reduced Total Cost of Ownership is achieved over three years
Energy efficiency is an issue that concerns all who are involved with the design and operation of data centres. The cooling function in general, and the operation of water chillers in particular, are large consumers of power and as such, require focused efforts to improve overall energy efficiency.
Water chillers account for between 60 and 85% of overall cooling-system energy consumption. Consequently, data centres are designed, where possible, to keep usage of chillers to a minimum and to maximise the amount of available “free cooling”, in which less power-hungry systems such as air coolers and cooling towers can keep the temperature of the IT space at a satisfactory level.
One approach to reducing water chiller energy consumption is to design the cooling system so that a higher outlet water temperature (CHW) from the chillers can be tolerated while maintaining a sufficient cooling effort. In this way, chillers consume less energy by not having to work as hard, and the number of free cooling hours can be increased.
As with any complex system, attention needs to be paid to all parts of the infrastructure, as changes in one area can have direct implications for another. A new White Paper from Schneider Electric, the global specialist in energy management and automation, examines the effect on overall cooling system efficiency by operating at higher chilled water temperatures.
White Paper #227, “How Higher Chilled Water Temperature Can Improve Data Center Cooling System Efficiency“, outlines the various strategies and techniques that can be deployed to permit satisfactory cooling at higher temperatures, whilst discussing the trade-offs that must be considered at each stage, comparing the overall effect of such strategies on two data centres operating in vastly different climates.
Among the trade-offs discussed were the need to install more air-handling units inside the IT space to offset the higher water-coolant temperatures, in addition to the need for redesigned equipment such as coils, to provide adequate cooling efforts when CHW (chilled water temperature) exceeds 20C. The paper also advises the addition of adiabatic, or evaporative, cooling to further improve heat rejection efficiency. Each approach requires an additional capital investment, but results in lower long-term operating expenses due to the improved energy efficiency.
White Paper 227 details two real-world examples in differing climates; the first is in a temperate region (Frankfurt, Germany) and the second in a tropical monsoon climate (Miami, Florida). In each case, data was collected to assess the energy savings that were accrued by deploying higher CHW temperatures at various increments, whilst comparing the effect of deploying additional adiabatic cooling.
The study found that an increased capital expenditure of 13% in both cases resulted in energy savings of between 41% and 64%, with improvements in TCO between 12% and 16% over a three year period.
Another inherent benefit of reducing the amount of energy expended on cooling is the improvement in a data centres PUE (Power Usage Effectiveness) rating. As this is calculated by dividing the total amount of power consumed by a data centre by the power consumed by its IT equipment alone, any reduction in energy expended on cooling will naturally reduce the PUE figure.
The Schneider Electric study found that PUE for the two data centres examined was reduced by 14% in the case of Miami and 16% in the case of Frankfurt.
White Paper #227 “How Higher Chilled Water Temperature Can Improve Data Center Cooling System Efficiency” is immediately available for free download by clicking here, or visiting http://www.apc.com/wp?wp=227
About the authors
Paul Lin is a Senior Research Analyst at Schneider Electric’s Data Center Science Center. He is responsible for data centre design and operation research and consults with clients on risk assessment and design practices to optimize the availability and efficiency of their data centre environments. He holds a master’s degree in mechanical engineering from Jilin University
Victor Avelar is the Director and Senior Research Analyst at Schneider Electric’s Data Center Science Center. He is responsible for data centre design and operations research and consults with clients on risk assessment and design practices to optimize the availability and efficiency of their data centre environments. He holds a bachelor’s degree in mechanical engineering from Rensselaer Polytechnic Institute and an MBA from Babson College.
John Bean Jr is the Director of Innovation for Racks and Cooling Solutions at Schneider Electric. Previously he was World Wide Engineering Manager for Cooling Solutions at Schneider Electric, developing several new product platforms and establishing engineering and laboratory facilities in both the USA and Denmark. Before joining APC, John was Engineering Manager for other companies involved in the development and manufacture of mission-critical cooling solutions.
About Schneider Electric
Schneider Electric is leading the Digital Transformation of Energy Management and Automation in Homes, Buildings, Data Centers, Infrastructure and Industries.
With global presence in over 100 countries, Schneider is the undisputable leader in Power Management – Medium Voltage, Low Voltage and Secure Power, and in Automation Systems. We provide integrated efficiency solutions, combining energy, automation and software.
In our global Ecosystem, we collaborate with the largest Partner, Integrator and Developer Community on our Open Platform to deliver real-time control and operational efficiency.
We believe that great people and partners make Schneider a great company and that our commitment to Innovation, Diversity and Sustainability ensures that Life Is On everywhere, for everyone and at every moment.
Hashtags: #datacentre #PUE #Efficiency #Cooling #EcoStruxure
Follow us on:
SOURCE Schneider Electric
To post and circulate your own press release on FIR and the eTN Network please click here
Comments are closed here.